SPECIFICATIONS FOR HEATING FILM
Listings: ETL/UL Listed for U.S. under UL 1693 ETL 4007353, CE 120509, TUV K5140/E112
Controls: Heating Film must be controlled by a CarbonicHeat approved line voltage floor heat-sensing thermostat.
Voltage: 120 VAC Max 100 sq. ft. (9.29 sq.m) 50/60hz, 240 VAC Max 200 sq. ft. (18.58 sq.m) 50/60 Hz
Up to 2000 square feet may be installed using slave thermostatic units.
Watts: 15 W/sq. ft. (51 Btu/sq. ft.), 166.1 W/sq.m
Maximum circuit load: 15 Amp
Maximum circuit overload protection: 20 Amp breaker GFCI: (Ground Fault Circuit Interrupter) required for each circuit (included in the thermostat control).
Maximum bend radius: Not to exceed 90 degrees. Do not crease Heating Film.
Maximum exposure temperature: (Continuous and storage) 150ºF (65.5ºC)
Minimum installation temperature: 50ºF (10ºC)
Installation must be performed by qualified persons, in accordance with local codes, ANSI/NFPA 70 (NEC Article 424), and CEC Part 1 Section 62 where applicable. All electrical work must be installed in accordance with Article 424 Part IX of the National Electric Code (NEC) ANSI/NFPA 70. “STATEMENT OF NATIONAL ELECTRIC CODE PRODUCT COMPLIANCE (NEC). This product from Carbonic Heat™ Products, LLC is compliant to Article 424, Part IX of the National Electric Code (NEC), “Electric Radiant Heating Sheets and Heating Sheet Sets” and as a Heating Sheet Set. Electrical installations must use a Terminal Junction Assembly manufactured only by Carbonic Heat™ Products, LLC per NEC 424.96 (2)”.